KTA50-GS8 Industrial Power Generators 1500KVA Cummins Power
Genset Data: 400/230V, 50Hz, 3 Phase 4 Pole, 1500RPM, Power Factor 0.8.
1. Prime power 1500KVA, standby power 1650KVA.
2. Powered by Cummins engine.
3. Original Enggaalternator.
4. Delixi air breaker.
5. Electric start with batteries.
6. Deep sea controller.
7. ATS is for option.
- - - -
Product Name | 1500KVA Diesel Genset | Model | SCE1500 |
Rated Power | 1200KW / 1500KVA | Standby Power | 1320KW / 1650KVA |
Engine Brand | CUMMINS | Alternator Brand | ENGGA |
Voltage | 400/230V | Current | 2160A |
Frequency | 50Hz | Running Speed | 1500RPM |
Phase | 3 | Power Factor | 0.8 |
Dimension | 580022802500 mm | Weight | 13000 KG |
- - - -
- - - -
Diesel Engine |
Brand | CCEC Cummins |
Model | KTA50-GS8 |
Number of Cylinders | 16 |
Rotating Speed | 1500RPM |
Cylinder Arrangement | 60 Vee form |
Cycle | Four stroke |
Aspiration | Turbocharged and air-to-air intercooled |
BoreStroke(mm) | 159 x 159 |
Displacement(L) | 50.3 |
Compression Ratio | 14.9:1 |
Speed Governor | EFC speed governor |
Cooling System | Closed cycle water-cooled with fan drived by belt |
Speed Stability (%) | 5% |
Total Lubrication System Capacity (L) | 178 |
Fuel Consumption at 100% Load | 204 g/kw.h |
Starting Method | DC 24V Electrical starting |
- - - -
- - - -
Brand | Engga |
Model | EG450-1200N |
Number of Phase | 3 |
Connecting Type | 3 Phase and 4 Wires |
Number of Bearing | 1 |
Protection Grade | IP21 |
Altitude | 1000m |
Exciter Type | Brushless ,Self-excited, AVR automatic voltage regulation |
Insulation Class | H |
Telephone Influence Factor (TIF) | 50 |
THF | 2% |
Voltage Regulation, Steady State | 1% |
Transient State Voltage | -15%~+20% |
- - - -
Introduction of Diesel Generator:
A Diesel Generator (DG) is a combination of diesel engine with electrical generator (often called an alternator) to generate electricity. DG sets are used in places that have no connection to power grid, and as emergency power-supply if the grid fails. In other words, DG sets remain the number one choice for standby and emergency power systems. DG sets are selected based on the electrical load they are intended to supply.
SCOPE OF SUPPLY
1. DIESEL ENGINE
1.1 Engine which includes wet type cylinder, direct injection combustion chamber, exhaust turbocharger, water cooling, electronic governor, etc.
1.2 Fuel system, which includes, fuel pump, strainers or filters, etc.
1.3 Air intake and exhaust system, which includes air filter, exhaust silencer, bellow, all intake and exhaust piping, cablings, instruments, valves and settings, etc.
1.4 Cooling system, which includes radiator with water level alarm and indicator, thermostatic switch, thermostatic heater, engine shaft mounted fan, all interconnecting piping, cablings, instruments, valves and settings, etc.
1.5 Lubricating system includes pumps, oil sumps, oil strainers and filters, all interconnecting piping, instruments, valves and settings, etc.
1.6 Starting system, which includes 2 sets of batteries, a set of AC charger, and interconnecting piping, cablings, instrument, valves and settings, etc.
2. AC SYNCHRONOUS GENERATOR
2.1 Generator, which includes exciter, rectifier, AVR, shaft mounted fan if required.
2.2 All interconnecting piping, cablings, instruments, valves and settings, etc.
3. COUPLINGS AND GUARD
3.2 Coupling Guard
4. CONTROL PANEL
4.1 Local automatic control panel
5.1 Common base plate
6.1 Generator Set Installation Manual
6.2 Generator Set Operation and Maintenance Manual
6.3 Generator Set Control Panel Manual
6.4 Engine Manual and Quality File
6.5 Alternator Manual and Quality File
6.6 Factory Acceptant Test Report