625KVA Industrial Diesel Generators , 3 Phase Cummins Diesel Genset
Genset Data: 400/230V, 50Hz, 3 Phase 4 Pole, 1500RPM, Power Factor 0.8.
1. Prime power 625KVA, standby power 688KVA.
2. Powered by Cummins engine.
3. Original Engga alternator.
4. Delixi air breaker.
5. Electric start with batteries.
6. Smartgen controller.
7. ATS is for option.
- - - -
Genset model | SCE625 |
Genset rated power | 500KW/625KVA |
Rated voltage | 400/230V (adjustable) |
Rated current | 900 Amps |
Frequency | 50 Hz |
Power factor | 0.8 Lagging |
Connecting type | 3 phase 4 wire |
Cooling system | Closed cycle water-cooled with fan, water tank |
Overall dimension (LWH) mm | 330012501850 |
Gross weight (kg) | 5000 |
Diesel Engine |
Brand | CUMMINS |
Model | KTAA19-G6A |
Engine type | 6 cylinders in Line,4 stroke, direct injection |
Aspiration | Turbocharged and air-to-air aftercooled |
Rotating speed | 1500 RPM |
Engine cooling system | Water-cooled |
Speed governing system | Electronic speed governor |
Starting method | By 24V batteries |
Engine filter system | Dry type air filter ,fuel filter, oil filter, water filter |
Displacement(L) | 19 |
BoreStroke(mm) | 159159 |
Compression ratio | 13.9: 1 |
100% Load fuel consumption (l/h) | 121.2 |
Lube capacity(L) | 38 |
Brand | ENGGA |
Model | EG355-500N |
Excite type | Brushless self-excited AVR regulation |
Connecting type | 3 phase 4 pole |
Steady frequency change | 0.50% |
No load voltage | 95%-105% |
Steady voltage | 1% |
Insulation class | Class H |
Protection grade | IP21 |
- - - -
Why Cummins Powered Gensets?
1. Cummins engines which are made in China with the same standard of the US Cummins keep the quality almost the same as the US Cummins.
2. More than 90% of the Engines components and spares are made in China which keeps the cost much lower.
3. Cummins engines are universally just as Cummins factories all around the world; all the spares are universal which make the maintenance and reparation very simple.
4. Cummins has worldwide after-sales network, to whom you can get technical support and spares right near your house.
5. Engineers are more familiar with Cummins engines because they are most widely use in every filed and everywhere around the world.
INSPECTION AND TEST
1.1 Each engine shall be tested at manufacturers workshop to certify the engine output and fuel consumption in accordance with the site operating condition specified by purchaser on the specification datasheet.
1.2 All relevant information drawings pertinent to the testing and test procedure shall be transmitted to the purchaser in advance of the test date notification.
1.3 The purchaser shall call for additional testing if test results are unsatisfactory or marginal. Any equipment rejected shall be repaired or replaced to the purchasers satisfaction and tests shall be repeated.
1.4 Any unsatisfactory material, equipment, installation, or workmanship shall be replaced or repaired to the purchasers satisfaction at the manufacturers cost.
1.5 The engine and generator shall be tested individually in accordance with relevant standards specified above.
1.6 The completed and individually tested engine and generator shall be assembled onto the base plate with all auxiliaries, instruments and controls for a complete test of the generator set.
Introduction of Diesel Generator:
A Diesel Generator (DG) is a combination of diesel engine with electrical generator (often called an alternator) to generate electricity. DG sets are used in places that have no connection to power grid, and as emergency power-supply if the grid fails. In other words, DG sets remain the number one choice for standby and emergency power systems. DG sets are selected based on the electrical load they are intended to supply.